RGS Buy Goulds Pumps RGS submersible sewage pump online. ITT Goulds watewater pumps from Locke Well & Pump Orlando Florida. GOULDS PUMPS RGS Residential Grinder Pump, Cast Iron, 2 hp: Amazon. com: Industrial & Scientific. Goulds Pumps RGS Explore Goulds Pumps on Octopart: the fastest source for datasheets, pricing, specs and availability.
|Country:||Bosnia & Herzegovina|
|Published (Last):||12 August 2005|
|PDF File Size:||9.66 Mb|
|ePub File Size:||3.9 Mb|
|Price:||Free* [*Free Regsitration Required]|
The power cable is severe duty rated, oil and water resistant, with a epoxy seal on the motor end providing a second moisture barrier in case of outer jacket damage and to prevent oil wicking. Add a Rfs2012 You need to sign in to add a review. This communication provides access to our Privacy Notice. Rsg2012 Electro-coat paint process protects all casting surfaces. Upper and lower ball bearings for precision positioning of parts and to carry all radial and thrust loads.
Drive Assembly The grinder assembly shall consist of two hardened components mounted directly below the impeller.
Click here to learn more about how this cookie is managed by Twitter. The motor is fully submerged in a high grade turbine oil-filled chamber for more efficient heat dissipation, permanent lubrication of bearing and mechanical seals, and protection against outside environment. Power Cable Severe duty rated, oil and water resistant.
The website cannot function properly without these cookies. The ball bearings shall be designed for a B life of 30, hours minimum. No external capacitor kits required.
P suffix equals a 20′ long cord with plug.
The impeller shall be designed such that the rotating cutter vanes can be accurately aligned to the impeller vanes for proper solids passage through the pump. Balanced for smooth operation.
RGS – Buy Goulds pumps RGS submersible sewage pump – $1,
Impeller Information The impeller shall be semi-open, non-clog, with ejector pump out vanes on the top of the impeller shroud for protection of the mechanical seal and to improve hydraulic balance. Epoxy seal on motor end provides secondary moisture barrier in case of guolds jacket damage and to prevent oil wicking. Rys2012 hardware shall be series stainless steel. The grinder assembly shall consist of two hardened components mounted directly below the impeller.
Copyright Xylem Inc. Adaptable for guide rail system. Rotating cutter and cutter ring: Sleeve type bearings shall not be considered equal and shall not be allowed. This means that every time you visit this website you will need to enable or disable cookies again. The mechanical seal faces shall be constructed of silicon carbide contacting silicon carbide.
These cookies allow us to count visits and traffic sources, so we can measure and improve the performance of our site.
RGS2012 – Goulds Pumps Submersible Grinder Pump
Designs which require a specific torque on the casing bolts or which require rectangular gaskets or sealing rings shall not be allowed. They help us know which pages are the most and least popular and see how visitors move around the site. The motor shall be provided with ball type anti-friction bearings which shall support the heavy-duty rotor shaft and to handle all radial and axial loads imposed by the impeller while limiting shaft deflection at the mechanical seal faces.
Locke Sidebox Header Secure Online Shopping We take your privacy and security serious. You can adjust all of your cookie settings by navigating the tabs on the left. We are committed to ensuring that the individuals whose details we hold understand our privacy practices.
O-Ring Assures positive sealing against contaminants and oil leakage. Xylem uses ‘cookies’ and ‘media beacons’.
Motors shall be equipped with on winding thermostats connected in line to provide automatic reset operation. The spring system shall be constructed of series stainless steel metal components and Buna-N elastomers. Stationary cutter ring is reversible for extended service. The motor shall gouldds rated for continuous duty under full nameplate load while at partial submergence in the station.